Replaced the dual capacitor, start capacitor, and relay on a Trane Heat Pump. Cycled on cooling and found condenser fan motor shorted to ground. Replacement part ordered.
Columbus reynoldsburg pickerington weekend emergency heating and cooling service. Goodman Hvac repair
After hours HVAC service. Blower motor replaced on 2004 Goodman Furnace. System fully operational at this time.
Diagnosis of 1992 Trane Air Conditioning System issues. Repairing vs replacement options given to customer.
Trane A/C System recharged with 1 lb of R-22 Freon. Cleaned off the outdoor condenser coil and system cooling at this time.
2002 Bryant Air Conditioner recharged with 0.5 lbs of R-22 Freon and Easy Seal added. Replaced the Dual Capacitor and the unit is cooling well.
Trane A/C diagnostic service appointment. Confirmed bad capacitor and replacement part being ordered under warranty.
Diagnostics service performed on York A/C System. Recharged system with 2 lbs of R-410A Puron. Further recommendations given on prolonging the system life.